1. Introduction The awareness of the new prevention needs and the constant and continuous technical evolution has led the standardizer to...
The awareness of the new prevention needs and the constant and continuous technical evolution has led the standardizer to analyze more in-depth the problems related to the use of electrical and electronic equipment in environments with the presence of dusts during handling and storage.
In fact, the problem of explosions generated by powders was not much considered in previous years. It was then realized its true danger, and with difficulty, the designers and the public opinion accepted that an explosion could be generated even by the presence of dust without the addition of flammable gases.
Considering that dust explosions are not very frequent, but if they occur, the consequences are very dangerous and notoriously superior to a fire delimited in a small and well ventilated environment, it is necessary to calculate the correlated risk: R = P x C, where R corresponds to the acceptable Risk (the risk depends on the protection at first instance of persons and in second instance of things), P corresponds to the Probability that the risk is manifested and C corresponds to the Consequences arising from the occurrence of the risk, effectively highlighting how the determination of risk is of fundamental importance.
For these reasons, it is essential that the designer, the manager and maintenance operator of such equipment have all the regulatory tools always present and constantly updated, in order to correctly design and size the electro-instrumental equipment and then to keep them constantly efficient, respecting the protection of people and things.
Typical cause of fire in a woodworking shop (source Trentino region)
Typical damage resulting from the explosion (source Trentino region)
The following list of the regulations describes the fundamental criteria to be adopted for the construction, installation and maintenance of electro-instrumental equipment. They are subdivided into national regulations (CEI EN), Community regulations (EN) and international standards (IEC). We will list only the final part of the standard, omitting the prefix (CEI or EN or IEC).
There are also a further series of standards aimed to the maintenance and repair of equipment such as:
The peculiarity of 'Ex d Ex tb' control panels consists in the fact that, inside them, it is not necessary to install equipment with an Ex component certificate, but industrial equipment is enough. Outside, must be installed only operators complying with the relevant Ex regulations.
Our panels are designed in compliance with the reference standards 60079-31, 60079-32-1 and 60079-32-2, with particular observance, in the composition, of the maximum allowable power dissipations relative to the maximum ambient temperatures for which they were designed: + 40° C, + 55° C or + 60° C.
Inside the control panels can be mounted electrical and instrumental equipment, in quantities depending on the size of the panel board and with a total sum of the dissipations that must remain within the power limits defined for each panel. The power dissipations correspond to the certificate values at the above-mentioned ambient temperatures. Examples of equipment that can be mounted inside the cabinets are terminals, analog and digital instruments, measurement and control devices, circuit breakers, etc. Our ATEX and IECEx certified battery packs can be installed also.
Considering what is listed above, it is clear that the duties of the designer first and then of the maintenance technician are of fundamental importance for the correct sizing and management throughout the life cycle of the plant where these types of electrical panels will be installed.
Cortem Group developed a new series of Control Panels suitable for installation in environments with explosive or flammable dusts, with ‘Ex tb IIIC T80 ° C Db’ IP66 method of protection, according to the 60079-31 Standards. In the paragraph 4.2.1, it defines the IP 6X protection degree, considering the first number relevant to the penetration of solid bodies. Cortem Group safeguards also by the penetration of liquids with the second digit "6", realizing panels with IP66 degree of protection. They are divided into three specific categories such as:
The installation of terminals, analog and digital instruments, measuring and control devices, automatic circuit breakers, etc., is provided for all three types of switchboards.
The range of Cortem Group panel boards is completed by a series of control, command, measurement and signaling operators made in compliance with the standard requirements and covered by a specific ATEX and IECEx certificate: